- Installation into pipelines as inline deflagration flame arrester e. g. for the protection of ignition gas lines of gas consumption devices (flare of biogas plants).
- Applicable for all materials of the explosion groups IIA1 up to IIC with a maximum experimental safe gap (MESG) < 0.5 mm.
- Operating from both sides, for a maximum operating pressure of 1.1 bar abs. and a maximum operating temperature of 60 °C.
- The distance between the ignition source and the armature may not be larger than 30 x the inside pipe diameter.